|MTS Metallurgical Testing Services|
|Download the PDF:
Square surface mounted spigots load test (193 downloads)
|To||Sorrento Glass||Report No||MTS-18494 SG|
|1 / 7 Hector St Osborne Park WA 6017||Issue Date||04/08/2014|
|Order No.||G. Vile||Test Date||20/06/2014|
MTS Metallurgical Testing Services was engaged to conduct load tests on a pool fence spigot to the requirements of Australian Standard
AS 1926.1 – 2012.
|ID||Item/Heat No.||Dimensions/Type/Details||Finish||Overall Assessment|
|18494/01||Square Spigot||50mm Square Bplted Base Duplex stainless
Examinations & Tests
A visit was made to the test site to verify the installation arrangements against supplied drawings and to conduct a load test.
The results of the tests reported herein COMPLIED with the requirements of the stated standard.
Metallurgical Testing Manager
The 40mm round bolted base spigot
The spigot was installed in accordance with the details of this drawing, modified to suit the 100mm thick floor at the test site.
|Test Specification||AS 1926.1 – 2012, Appendix C||Test Procedure||MTS-TP3.1 Compression Tests – Products|
|Specimen ID||Test Load (N)||Deflection Under Load (mm)||Permanent Distortion (mm)||Observations||Assessment|
|188494/01||330||30.0||2.0||No damage or loosening evident.||COMPLIES|
The Bolted Base Square Spigot under test load.
Requirements:No breakage or signs of fracture or loosening of any part. Maximum Permanent Distortion: 6mm.
Remark:A specially made stiffened test jig was used to simulate the effect of an in-service load applied at 1200mm above ground level.
MTS-18493 SG This document shall not be reproduced, except in full.
Copyright © 2010~2014 Dataprime Solutions Pty Ltd. All Rights Reserved. 119903838567